>>Automatic removal of single-phase grounding fault
When the single-phase grounding fault happens in user branch line, the boundary switch open automatically, the other branch user of substation and feeder line do not feel the failure.
>>Automatic isolation interphase short circuit fault
The user side happens phase short-circuit fault, boundary switch off immediately after trip protection in substation. Substation coincidence, the fault line is automatically isolated, the other branch user on the feeder to restore power supply quickly (the equivalent of a transient fault).
>>Fast locate the fault position
Boundary switch protection action caused by user fault branch, only responsibility users power fault and the initiative to submit fault information, the power company can quickly send officials to troubleshooting; if the boundary switch equipped with such as a communication module, information will be submitted to the power management center autimatically.
>>To monitor the user load
Boundary switch can be configured with wired or wireless communications accessories, monitoring data will be transmitted to the power management center, realize remote real-time data monitoring of user load.